NOTES : 
****
TRAVAUX POUR COMPLETER DOSSIER CSA
(VERIFIER AVEC FGAUTHIER SI FACTURABLE AU CLIENT OU PARTI 
CONTRACT CASA)
****
AVEC MDION ET SAMI
****
VERIFICATION DU SECHOIR STRAHL POUR DETERMINER LES 
MODIFICATIONS A FAIRE POUR METTRE EN ORDRE ET PASSER APPROBATION 
CSA
*****
NOTE : CLIENT NE VEUT PAS QU\'ON PARTE LES MOTEURS CAUSE PENALITE 
SUR FACTURE HYDRO QUEBEC, IL VA FALLOIR CONTACTER CLIENT ET 
CEDULER DANS UN MOIS OU IL VA AVOIR UTILISATION DU PLANT)

-LPG EST BYPASSER ET PAS LE BON RANGE
-HPG DOIS ETRE REMPLACER PAR MANUAL RESET
-BRULER DEVRA ETRE AJUSTER LORSQUE LES MODIFICATIONS SERONT 
FAIT, RECOMMANDE D\'AVOIR EN MAIN LES SPRING POUR LES REGULATEURS 
BYPASS AINSI QUE POUR LE REGULATEUR PRINCIPALE
-A VERIFIER AVEC CONTRACTEUR DE GAS SELON MAXIME MANQUE UNE 
PIECE?
-A VERIFIER PRESSION D\'OPERATION, FORT PROBABLE IL VA FALLOIR 
AJUSTER PRESSION DE LIGNE POUR 5PSI A L\'ENTREE IL EST A 13-14PSI 
PRESENTEMENT
-LES VENT NE SONT PAS A 10\' DE L\'ENTREE D\'AIR IL DEVRONT ETRE 
RALLONGER.
-IL Y A BEACOUP DE BOUT DE TUYAUX EN ACIER NOIR QUI DEVRAIS ETRE 
PEINTURER SELON LE CODE.
-LOW AMBIENT TEMPERATURE NON FIXER DE FACON LEGALE DANS LE 
PANNEAU DEVRAIS FAIRE PLACE ET INSTALLER CORRECTEMENT
-TRANSFO 600 A 120V DANS LE PANNEAU BRULEUR LES TERMINAUX SONT 
EXPOSER ET RISQUE D\'ELECTROCUTION, RECOMMANDE DE RAJOUTER DES 
HEAT SHRINK POUR PROTEGER.
-HTL (HI LIMIT CONTROLER) DEFECTUEUX, DOIS ETRE REMPLACER, AUSSI 
MODELE NON CONFORME
-HTL DEVRAIS ETRE RELOCALISER DANS PANNEAU INTERIEUR
-BESOIN FIL SHIELDER TRIPLE, CONNECTEUR, BOITIER PVC POUR LA SONDE 
PT100 DU HTL
-FILLAGE POUR ROTOBINE SORTIE DU SECHOIR NON-FIXER
-UN DES TUYAUX DES AIRFLOW SWITCH SERA A REMPLACER (TUYAUX 
PLIER)
-LES CIRCUIT ESTOP SONT TOUS BYPASSER ESTOP ET CAPTEURS DE 
PORTES
-QUELQUES CAPTEURS DE PORTES AURONT BESOIN ETRE ENLIGNER.
-A VERIFIER LE CICRUIT AVEC TIMER POUR LES UV SENSOR, IL Y A PEUT-
ETRE ERREUR DE BRANCHEMENT
