NOTES : 
DEMARRAGE SECHOIR+STATION GAZ NATUREL.

STATION GN PURGE DE LA VALVE RELEIF LORSQUON DEMARRE LE SECHOIR.

ENLEVER REGULATEUR INSTALLER PAR FERNAND DENIS, MEME PROBLEME AVEC LA STATION.

SI ON REDUIT PRESSION AU SECHOIR A 3PSI LE PROBLEME PERSOSTE QUAND MEME.

EMBRIDGE DIT IL FAUDRAIS UNE LIGNE 2” JUSQU’AU SECHOIR MAIS JE NE CROIS PAS QUE C’EST LE PROBLEME.

INSTALLER UN SEQUENCEUR AVEC RELAIS POUR PARTIR SECHOIR SUR PETIT FEU POUR EVITER QUE EMBRIDGE FERME LA 
STATION ET QUE LE CLIENT 
PUISSE SECHER EN FIN DE SEMAINE

EMBRIDGE SERA DE RETOUR LUNDI VERS 11H00 ET CA PRENDS UN TECHNICIEN SUR PLACE POUR LE SECHOIR


PIECES : 


VEHICULES : 
DEPART 7H55